All consumables and original spare parts for MTC POWER SYSTEM brand of generators are available at our area dealers. Furthermore, you can notify your demands for spare parts of all kinds of engines, alternators and generators to MTC to obtain information and quotes about them.
Please respect the schedules given in the maintenance manual and user's manual delivered with your generator. Please remember that a number of factors can shorten the intervals described in said schedules: operation startup frequency, operation time, load level, quality of lubricants and fuel used, ambient temperature, dirty-dusty environment, etc. Responsibility for timely maintenance, check and replacement of consumables (lubricant, filters, V-belts, antifreeze, injectors, etc.) remains with the user. You are recommended to arrange a general check, adjustment and test every 2 or 3 months. General maintenance must be made and lubricants and filters must be replaced once a year even if the operation hours described in the schedule has not elapsed. Furthermore, you should test your generator under load for 10 to 15 minutes once a week.
Please apply to your local MTC area dealer for reliable, accurate and economic maintenance services and checks.
Running a generator above the capacity rating indicated on its label is as much wrong as running it below related capacity rating, because its service life might be shortened and it might suffer serious damage.
This is especially true for generators having large capacity ratings.
Minimum load allowed for standby generator sets is 30% of its total rating.
The following problems might happen if a generator runs without load or under low load:
- Its exhaust and air suction system might suffer lubricant or fluid leaks
- Carbon deposits might accumulate on its cylinder liners or exhaust manifold
- Parts of its engine might be damaged due to wear
- Lubricant might get thinned to cause the lubrication quality to decrease
- White smoke might be emitted
All MTC products are warranted against part and manufacturing faults. Please review the documents delivered with your product or contact your dealer for detailed information about the terms and scope of warranty.
It refers to the number of revolutions of your generator set per minute. It is usually 1,500 or 3,000 RPM for engines and alternators at 50Hz, and 1,800 or 3,600 RPM for 60Hz.
Category (standby, prime, continuous) of your generator set has been indicated on its label. If a generator is used above its rating, the following problems might happen:
- Engine might overheat
- Wearing of the engine might increase
- Alternator's windings might overheat
- Lubricant might get thinned and lubrication pressure might decrease
- Service life of the engine might shorten
Exhausts, bodies and fans of all generator sets emit a noise. Depending on the type of the site where the generator is installed, certain measures are necessary.
Acoustic insulation cabins provided by MTC are an optimum solution to ensure maximum noise control.
Calculation of the generator capacity needed by a user requires specialty and depends on various factors.
Related factors include the operation category, properties of the loads, ambient conditions, and optional products.
You can get assistance from MTC or its area dealers.
Generators can contain different units and options depending on their brand.
Main units are:
- Chassis - Daily fuel tank
- Control panel
- Transfer panel
Selection of a site for your generator and installation of the same must be made in a correct way to ensure it to have a long and problem-free service life. You can apply to MTC POWER SYSTEM for detailed information at every stage.
- Selection of a site: If the generator will be installed indoors, ventilation and exhaust pipes must be installed. If it will be installed outdoors, a cabin and a platform must be erected.
- Floor: The floor must be flat and smooth to prevent accumulation of water. A platform can be built to ensure a proper height. If the generator will be installed outdoors, it must be placed in a shed.
- Ventilation: Heat emitted by the alternator, engine and radiator of a generator set must be removed from the system by a fan installed between the engine and the radiator, therefore the generator must be installed in a well-ventilated room or area. Such room or area must get fresh air.
- Fuel system: Clean fuel must be fed to the generator on a continuous basis. It can be fed by manual or automatic mode.
- Exhaust system: Noise and emissions emitted by the exhaust system of the engine must be reduced and released to atmosphere in a safe way.
- Electrical system: All electrical connections must be made in accordance with the drawings delivered with the generator set and the general applicable rules.
All engine and alternator manufacturers comply with related Standard. These terms define the category in which a generator will run.
- Standby power: Power generation for a limited period under variable load. It can work 200 hours a year under 70% load in average. It is used as standby power supply in case of municipal power failure. It must not be overloaded.
- Prime power: Continuous power generation under variable load. Its average load must be 70%. It can be overloaded by 10% for 1 hour every 12 hours.
- Continuous power: Continuous power generation under fixed load. Load can be 100% in average. It must not be overloaded.
Depending on the circumstances, your generator might be overloaded or underloaded. In this case its service life can be shorten, its operational efficiency can decrease, its service life can shorten, and it can suffer damage, as explained elsewhere above.
You should ensure your generator to be used for the category indicated on its label or explained by your dealer. This is especially important for its warranty too.
Fufel consumption of a generator depends on its load. MTC designs its fuel tanks in such a manner to allow the generator to run for at least 8 hours under full load. The lesser the load, the longer the operation time.
Every generator set must be tested under load for 10 minutes at least once a week. If you will not use your generator for a long time, please perform the instructions given in the Maintenance and User's Manual about storage. Storage is very important for the service life of generators and must be performed by an authorized service shop. After storage for a long time, the generator must be prepared for operation by an authorized service. This is especially important in terms of its warranty.
Developed & Design by AnzimaGroup. All Rights Reserved 2021